Our Work Around The World
11 kV harmonic filters supplied and commissioned at 3 steel plants in Central Gujarat. The power supply was cut by GETCO due to excessive harmonics generation which resulted in failures of pumps in the agricultural load. The harmonics were successfully mitigated and brought down below the norms set by GETCO.
Supply, erection, testing and commissioning of 15 MVAr, 132 kV capacitor bank at 220 kV substation at MSETCL, Solapur, Maharashtra.
6.6 kV and 3.3 kV Medium Voltage Automatic Power Factor Improvement systems supplied and commissioned at 3 pumping stations of Municipal Corporation of Greater Mumbai (MCGM) and Naval Dock, Mumbai.
Supply, installation and commissioning of 5th, 7th, 11th and 13th order Harmonic Filters at 440 V as system voltage in an island system at Chittagong, Bangladesh where power is supplied through 5 MVA diesel generators. The plant was not able to draw power beyond 3 MW but now able to draw greater than 4.2 MW after installation of tuned filters.
Supply, installation and commissioning of 5th and 11th order, 11 kV system voltage, Harmonic Filters to Steel industry at Yemen. Current THD level was brought down from 16% to < 5% and Voltage THD level was brought down from 11% to < 3%.
Supply and Construction 132 kV substation at Nigeria.